Trenchless Innovations provides air duct & sewer repair services that save property from significant digging or full duct replacement. We serve both residential and commercial clients of Schaumburg, IL and the surrounding areas.
Read our reviews and find out why your neighbors and local businesses consider us to be their local, trusted sewer & duct repair company in Schaumburg, IL.
for Schaumburg, IL
Our Reviews by City
Great Service works promptly and clean.
Tim - Schaumburg, IL
I would recommend Trenchless Innovations for all your sewer and heat duct work.
Wonderful job and great price
Glenn - Schaumburg, IL
Excellent service and great people to work with. Would highly recommend them
Video inspection of underground air ducts. Ducts are concrete with metal connections. Metal connections and plenum are showing heavy signs of rust. Suggest spray lining ducts with Duct Armor duct lining material to rehabilitate ducts.
Video inspection of underground air ducts. Ducts are metal with signs of rust. Suggest spray lining ducts with Duct Armor duct lining material to rehabilitate the rusty ducts and to provide a healthy breathing environment.
We cleaned all the underground duct work that was contaminated by a sewer leak, and applied our duct lining product to encapsulate the contaminated duct which was also a transite pipe.
Video inspection of underground air ducts. Ducts are concrete with metal ducts that are rusting. Plenum is severely rusted with standing water. Suggest installation of sump pit to control the water then spray linnng ducts with Duct Armor.
Video inspection of underground air ducts. Ducts are concrete possibly transite asbestos pipes with metal connections. Suggest spray lining ducts with Duct Armor to encapsulate the ducts.
Video inspection of underground air ducts. Ducts are spiral wound metal that is showing signs of rusting. Suggest spray lining ducts with Duct Armor Duct lining material.
Did a video inspection of the underground duct work finding the metal pipe was heavily rusted out and also had standing ground water in the ducts.
Video inspection of underground air ducts due to smell coming from the system. Ducts looked to be in good condition with no standing water. The customers floor drain was a bit low which could be allowing smells to enter into the house. Suggest filling floor drain and also extending all downspouts to prevent water from entering the duct system
Applied second application of our Duct Armor product to underground transite air ducts. The air ducts are now completely encapsulated and environmentally safe for the customer’s home.
Video inspection of underground air ducts that had water in them after heavy rain. Ducts are concrete possible transite asbestos ducts with metal connections. Suggest changing landscaping and downspouts outside then spray lining ducts with Duct Armor
Video inspected underground air buck system for customer complaining of low airflow in one part of the house. Inspection showed no damage, blockages or breaks in the system. Problem is due to a configuration issue. Suggest having an HVAC professional install a zoning system.
During the process of selling the house the home owner had to pass a radon test before selling the property, radon levels came back a little to high so before a mitigation company can put in a radon system to lower levels we had to seal all the underground duct work, but not only were radon levels high the piping used in the underground ducts are transite, which may contain asbestos, duct armor is a form of encapsulation for the transite pipe, leaving a new environmentally safe HVAC system.
Televising under slab floor air ducts. Ducts are concrete with metal connections.