Trenchless Innovations has been providing air duct & sewer repair services to solve problems for residential and commercial clients in Wheaton, IL and the surrounding areas since 2002!
View our service reviews to see why our cutomers rate us highly as their trusted air duct & sewer repair professionals in Wheaton, IL.
for Wheaton, IL
Our Reviews by City
Unique service that hopefully fixes my water issue
Rob - Wheaton, IL
The workers were very respective and nice. They tried to keep the mess down and cleaned up after themselves.
Response from Trenchless Innovations Inc.:
Thank you for your review, Rob! We are happy to hear that our team didn't leave a mess in your home and cleaned up after completing the job. We are delighted you had a good experience with us and we thank you for your business. Please don't hesitate to reach out to us again should you have any further questions. Thanks again!
Televised ducts under slab floor because of sewer smell in house. Found kitchen sink leaking into ducts and also tub and vanity leaking into ducts. Need plumber to fix drain lines then entire system should be retelevised to quote for encapsulation of ducts with Duct Armor duct lining material. Could not see ducts because of standing water at this time.
We are applying the second application of our rubberized duct lining material to all of the underground asbestos transite air ducts. The air ducts will be completely encapsulated and the air in the home will be safe for the customer to breathe.
We are applying the first application of our rubberized duct lining material to all of the underground asbestos transite air ducts. The air ducts will be completely encapsulated and the air in the home will be safe for the customer to breathe.
Televised ducts under slab floor. Ducts are concrete possibly Transite with asbestos with metal fittings and connections. Metal is showing slight signs of rust. Suggest spray lining ducts with Duct Armor duct lining material to encapsulate the concrete ducts.
Televised ducts under slab floor. Ducts are spiral wound metal that is slightly rusted. Plenum is rusted and has water standing in it. Downspouts need to be extended all around house. After taking care of the water issues the ducts should be spray lined with Duct Armor duct lining material.
We are installing a section of drain tile lower than the duct work under a slab section of the home to direct the water into a sump pit before it can rise up into the underground duct work.
VI's doe inspecting an underground air duct. Customer is getting water in the ducts during heavy rains. We will core a hole in the foundation wall in the basement under the lev l of the ducts. This will relive the water and then we will route this water to a sump pit in the basement.
Televised underground ducts, customer getting water in ducts during heavy rains. Recommend extending downspouts and installing sump pump to lower water table under slab.
Video inspection of underground air ducts. Ducts are metal and showing signs of rust and allowing debris in at joints. Suggest spray lining with Duct Armor to seal and restore the ducts.
Completed second application of Duct Armor. Under ground duct system is renewed.
Video inspection of under slab air ducts. Ducts are clay tile with separations in joints