At Trenchless Innovations, we pride ourselves on offering expert air duct & sewer repair services, as well as air duct and sewer video inspections to the residents and businesses of Highland Park, IL and the surrounding areas.
Our reviews speak for themselves! Read our customer reviews to see why our customers in Highland Park, IL are continually satisfied with our services.
for Highland Park, IL
Our Reviews by City
Televised ducts under slab floor. Ducts are mostly clay tile with the exception of one run that is metal. The one metal run is extremely rusted and deteriorated. The clay tile has debris at the joints. Suggest spin cast mortaring the system then spray lining with Duct Armor duct lining material. Customer has just recently installed drain tile around entire house to control any water issues.
We are applying the second application of our rubberized Duct Armor material to all of the underground asbestos transite air ducts. The air in the home will be environmentally safe to breathe.
We are cleaning all the underground duct work, and sealing the underground duct work, which is transite concrete pipe with metal connectors/ elbows, with our duct lining product.
Televised ducts under slab floor. Ducts are metal and are extremely rusted. Ducts should be spin cast mortared to restore the structure of the ducts then spray lined with Duct Armor duct lining material.
Televised under slab ductwork, found to be transite concrete ducts. Recommend encapsulating and sealing.
Video inspection of underground air ducts. Ducts are cardboard with metal fittings and elbows. Ducts are showing signs of water damage and also deterioration. Suggest spin casting a new concrete pipe inside the old ducts to restore structure and then spray lining ducts with Duct Armor duct lining material.
Video inspection of underground air ducts. Ducts are concrete possibly Transite asbestos pipes. Suggest spray lining the ducts with Duct Armor duct lining material to encapsulate the asbestos pipes.
Video inspection of underground air ducts. Air ducts are galvanized metal. Metal shows slight signs of rust and is allowing dirt to enter into the system through the joints. Suggest spray lining the system with Duct Armor duct lining material.
Video inspection of sewer line from an outside clean out. Sewer has heavy roots and an area that is leaking and causing a sink hole. Suggest installing a sewer liner in existing pipe through the clean out to seal the pipe and stop the root growth.
Video inspection of a sewer from a basement clean out. Sewer is clay tile with heavy root growth throughout. Suggest installing an outside clean out and then installing a liner in the sewer to repair the remaining 80 ft of sewer.
Video inspection of underground ducts.