At Trenchless Innovations, we pride ourselves on offering expert air duct & sewer repair services, as well as air duct and sewer video inspections to the residents and businesses of Hanover Park, IL and the surrounding areas.
Our reviews speak for themselves! Read our customer reviews to see why our customers in Hanover Park, IL are continually satisfied with our services.
for Hanover Park, IL
Our Reviews by City
We cleaned all the underground air ducts, then applied our trenchless cast to all the underground duct work to give weak rusted metal a strong structure, and finally applied two applications of our duct lining product to seal the entire underground system.
Vonorction of underground air ducts. Ducts are extremely rusted and deteriorated ducts need to be restored by Trenchless Casting a new concrete pipe inside the old ducts then spray lining the ducts with Duct Armor
Video inspection of underground air ducts. Ducts are metal and extremely rusted and have some standing water in one of the pipes and in the plenum under the furnace. Suggest Trenchless Casting a new concrete pipe inside the old pipe to restore structure to the pipe. After that the ducts should be spray lined with Duct Armor.
Video inspection of underground air ducts. Ducts are extremely rusted and are getting water at times of heavy rains. Customer needs to extend all downspout away from the house. After that they should get the ducts rebuilt with Trenchless Casting to restore structure and the spray lining ducts with Duct Armor.
Completed second application of Duct Armor to encapsulate and restore under slab duct work. We give a 15 year transferable warranty.
Televised underground duct work they were transite pipe(which may contain asbestos) with metal connectors and elbows. Also found minimal water in plenum box under furnace which is the lowest point in the system, so we recommend to run down spouts farther out away from house to eliminate water from getting under the slab and in the duct work. Once the down spouts were extended out and ducts were dry we were able to apply our duct armor product to encapsulate the transite pipe and seal the system.
Video inspection of underground air ducts. Ducts are transite asbestos pipes and should be spray lined to encapsulate the pipes.
Video inspection of under slab air ducts. Ducts are transite ducts with metal connections. Metal connections are rusting. There is also standing water under the furnace in the plenum. Customer should spray line ducts with Duct Armor